: GREENHECK BSQ/ 3/4 HP INLINE CENTRIFUGAL FAN //60/1: Home Improvement. Installation, operation and maintenance manual, General safety information • Read online or download PDF • Greenheck SQ and BSQ () User Manual. Centrifugal Square Inline Duct Fans Greenheck Fan Corporation certifies the model SQ and BSQ fans shown herein are licensed to bear the AMCA Seal.
|Published (Last):||18 August 2018|
|PDF File Size:||6.61 Mb|
|ePub File Size:||2.79 Mb|
|Price:||Free* [*Free Regsitration Required]|
Hanging rods to be supplied by others. The Online Industrial Exhibition.
Both options provide access panels on two sides. Each wheel is statically and dynamically balanced. A minimum of three duct diameters is required on the inlet and outlet of the fan to prevent system effect losses. Please enter your Email ID. It will take several duct lengths before the airow becomes laminar or smooth again after greenneck the turn.
These fans are specifically designed for inline applications. Fan wheels are centrifugal, backward inclined and constructed of aluminum.
Typical installation requires ductwork on the inlet and outlet side of the fan. Precaution should be taken in explosive atmospheres. Installation, Operation and Maintenance Manual. These compact inline fans are the ideal selection for indoor clean air applications including intake, exhaust, return, or makeup air systems where space is a prime consideration.
Model SQ is a direct drive centrifugal inline exhaust fan.
The model BSQ ducted inline fan must be installed with the motor accessible for greehneck and inspection. Remote Dial – Allows for remote, manual airow adjustments. Remember the duct length on the discharge side, should be approximately Single phase RPM motor.
Inline Fans (Models SQ and BSQ) – Greenheck – PDF Catalogs | Technical Documentation | Brochure
These compact inline fans are the ideal selection for indoor clean air applications including intake, exhaust, return or make-up air systems where space is a prime consideration. The hanging isolator support brackets are designed to permit mounting of the fan with the motor located on top, bottom or side.
Greenneck drive frame components may still be of galvanized construction to maintain structural integrity. The remainder of the model number is determined by the size and performance selected from the following pages. Prefer to pick it up yourself?. The most notable is reducing system effects.
Greenheck Bsq cfm 3hp Exhaust Fan | eBay
Open the catalog to page 9. Contact Seller Request a quote. Number of bids and bid amounts may be slightly out of date. The white cover also has a light fixture.
The gure 1 example shows the air being discharged into the corner. Figure 6 Horizontal Hanging or Base Greenhevk the catalog to page 7. It must be free to rotate without striking or rubbing any stationary objects.
Do not spin fan wheel faster than max cataloged fan RPM. Model BSQ ducted inline fans are designed for the exhaust, supply, or recirculation of air in a building. Laisser le moteur refroidir avant toute maintenance.
Greenheck SQ and BSQ (472058) User Manual
The base mount allows top motor location only. Open the catalog to page 6.
Both the fan and lter section feature removable access panels on both sides to remove and replace lters, making fan maintenance simple and fast. I took several p Open the catalog to page 2.